Perfect Earthings preaches and practices a proper and stringent earthing practice from identifying the favorable pit area, erection and installation followed by suggestive maintenance measures. It comes as a support to our earthing product and will be boon to our customers whom can let the experts to handle the erection and installation.
Consulting & Analysis
Consult the user’s requisite especially in the case of high end and sensitive operations
Identify the favorable pit area
Augur manually/Bore drilling with a diameter of 4.5” to 6” to a depth of 7 ½’ (2 m) / 11’ (3m)
In the dig /drill hole after adding moisture enhancer to the tune of 6” height and keep the earthing electrode upon the M.E
Add the Moisture enhancer along with water around the rod and by doing gentle thrust on the M.E to avoid the air crack in the pit.
The terminal point should be up above the pit level about 6”.
Wet the pit by watering regularly for 15-20 days till it gets stagnant to get familiar with moisture enhancer with the mother soil.
The earth resistance value can be taken after a week’s time.
Usage of Stainless Steel or Copper bolts & nuts to avoid the rust formation
Connect the equipment after getting satisfactory result.
Precaution & Handling
Minimum leave 5 ft distance from foundation to the earth pit
Minimum leave 10 ft distance in between the earth pit, if it is in series (more than one)
Avoid watery pit
Don’t mishandle the Electrode inside or outside the pit
Don’t break or bend or keep in slanting position while installation
Depend on the nature of the soil, water the pit at stipulated intervals